Fill each line of panels separately by installing valves on the interline fittings in order to purge the air efficiently.
Make sure that the pump is unplugged or switched to OFF. Turn the blue and red ball valves upright
Check the watertightness of the circuit (make sure the expansion vessel is disconnected from the circuit so as not to fill it with water).
Height difference between
|Expansion vessel inflation pressure||0,5 bar||0,7 bar||0,9 bar||1,1 bar||1,3 bar||1,5 bar||1,7 bar||1,9 bar|
|Fill pressure and service pressure||1,2 bar||1,4 bar||1,6 bar||1,8 bar||2,0 bar||2,2 bar||2,4 bar||2,0 bar|
Fill with glycol and rotate the filling pump for 30 minutes at a pressure lower than the maximum pressure given in the table given above.
During this time, purge so that the fluid exits without air bubbles, using the manual drain and the water hammer action of repeatedly closing/opening the drain valve.