For collective swiming pool
Yes it is recommended and our panels are already on several installation as you can see on the following installation : 120 DualSun hybrid panels for an energy-efficient green pool in Australia (AU)
No, it is not recommended to install DualSun SPRING panels for an indoor pool.
Here is the xemple of a residential project with the installation of 10 panelsDualSun SPRING not isolated to heat a 20 m² indoor pool.
- In the outdoor pool application, our panel provides approximately400 kWh/m²/year in Marseille.
- In the indoor pool application, the ambient air is already heated to the same temperature as the pool, often 28°C, and is saturated with humidity. Our studies thus show that thermal production drops to 150 kWh/m²/year due to this air/water temperature equivalence. This is why, so that the panels are used at their full power, we do not recommend installing these panels for an indoor pool.